Have HVAC Questions? Ask an HVAC Expert for Answers
Sounds like most likely a weak capacitor if this is a PSC motor.Do you have a capacitor with 2 brown wires from motor?
OK that cap is most likely the problem, Does it look puffy at all?http://i.imgur.com/12sSxri.jpg
It can still be bad or weak even if it looks new. Below shows how to test.If you do not have a meter to check capacitance you can take it off and take it to an appliance parts store and they will test it for you.Or you can replace it for about 10 bucks and that will probably solve your problem
If you have further questions, please let me know.
Thanks for letting me work with you.If my answer has been polite, professional,and thorough, please click one of the ratings before you go. If you still need help let me know!.Expert is not paid for assisting you until you rate answer.Feel free to follow up for 30 days at no additional cost. Bonus always appreciated if you feel justified.
To rate answer, please select one of the stars on the page.