Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, one minute while I get some information together.
Can you try to jumper the R to the G thermostat connections at the board in the unit to see if the blower runs?
ok no problem just make sure you have the safety switch depressed hen you have the panel off.
You have to jumper out the connections on the board not the wires
OK does anything light up on the board?
OK check the fuse on the board. There should be a slot fuse on the board.
OK then check for power to the unit either you lost power to the unit or possibly the board is bad.
Do you have 24 volts at the board if so do you have a condensate pump?
Follow the drain line from the AC coil on the furnace it would go to the pump if you have one