Have HVAC Questions? Ask an HVAC Expert for Answers
Hello,My name is ***** ***** I will do my best to assist you. I am looking over your question now and will respond shortly.
For the pilot you will need a new orifice.
And you are correct about the gas valve...you will need to swap the spring.
These conversion kits are very common and available many places.
you will also need to change the pressure from 3.5" wc to 10.5" wc
you are very welcome.
Also please note that once you rate the service at top of page you have 30 days of follow up. So if you need some help just let me know.