Have HVAC Questions? Ask an HVAC Expert for Answers
Can you attach photo of how it is wired?
Let me look it over
I have a couple of question?
Wrong diagram that is for someone else. Here
Make sure the fan wires are as follows.
Brown to F on capacitor
Orange to C on Capacitor
Black to FAN Motor terminal on board
OK so exactly what do you have?
Brown to the 2 prong
Orange to 4 prong
What color is other wire and is it going to FAN on board?
OK great so now does fan and compressor both come on as they should on call for cool?
Is led 1 and Led 2 either one on?
1. If both leds are off that indicates that we have no power to unit
If compressor will come on when pressing contactor and fan is coming on we know we have power to board so board is going to be bad if no lights are on
OK you will need to replace the board.
Do you want to by pass the board temporarily to have ac until you can get a board?
I understand. If we have power to board but leds are off, we definitely have a bad board.
If you have further questions, please let me know.
Thanks for letting me work with you.If my answer has been polite, professional,and thorough, please click one of the ratings before you go. If you still need help let me know!.Expert is not paid for assisting you until you rate answer.Feel free to follow up for 30 days at no additional cost. Bonus always appreciated if you feel justified.
To rate answer, please select one of the stars on the page.
Leaving a poor service rating will not automatically refund your money,but reflects poorly on your expert. You have to request a refund if not satisfied with the information provided being accurate.