Have HVAC Questions? Ask an HVAC Expert for Answers
Hello,My name is ***** ***** I will do my best to assist you. I am looking over your question now and will respond shortly.
does this model have a pilot tube/pilot assembly?
sorry I had went offline.
Remove the pilot tube from the side of the valve and see if pilot gas comes out of the valve. If it does you have a plugged pilot assembly. When can you check this?
The LP gas orfice is tiny. Just hooking new gas pipe to it can cause it to plug.
This is the most common issue with LP pilots.
If plugged remove pilot and clean out...
just keep this on your side and respond when you can.
so no gas comes out the pilot port on the valve when tube unhooked?
This means another issue. If you have a picture of the unit or the model number we can figure it out.