Have HVAC Questions? Ask an HVAC Expert for Answers
Hello,My name is ***** ***** I will do my best to assist you. I am looking over your question now and will respond shortly.
Ok basically we have a bad regulator or LP issue.
What happens is the system comes up to pressure when off. When opened the pressure in the line is depleted and not replaced fast enough by the supply. This means the regulator is not releasing the fl fast enough.
Just like water pressure...it slows until pump kicks on.
You need new or adjust regulator at tank