Have HVAC Questions? Ask an HVAC Expert for Answers
My name is Billy,
Can you post pictures of the install? Or we can go by description..I can also draw how it should be....will you be leaving this in a horiz position?
Thank you...was viewing factory drawings.
And you are saying the A coil open end is facing the blower?
The top of the coil should point towards blower .
air enters and is drawn through the large open end and through the coil.
If your air is entering the top part of coil it is backwards.
Now this is a Horiz left flow if I see the pics right....air enters right and goes out left?
And the flipping is is in the manual but you would just be doing it in reverse from the downflow configuration