Have HVAC Questions? Ask an HVAC Expert for Answers
Tell me a lot about the application and size of the building being served, and if you have natural gas in the area or not... electric make up air heat will cost a veritable fortune to operate in such a situation.
Thermostat is not a problem I will have to look up your model number on the Market'TPI hot pod though... do you have a model number on it?
We can go from there
That one will work great, it is 22 amp rated as well.
Its time to locate the 'finish and rate' link and click on it, that is the only way the company pays my time and expenses, in exchange I will hold the question open for any follow up you might need.
OK thanks, ***** ***** few minutes I will be right back
I am unable to find a line voltage programmable thermostat with fan controls rated at the 22 amps you need to be reliable.
My name is Billy. I am a bit confused by the design.
Why don't you just toggle the make up air to run when you heat and/or cool?
I have never seen make up air on a schedule other than occupied and unoccupied.
Plus the hot pods I have installed have a 24v control transformer built into the pod so the control is only 24v
I assume you are going with wall mount instead ceiling cassette with fresh air..
If you want to keep this simple and affordable...simply install a time clock (mechanical) like a paragon..or even a digital. Once store is open it gets power and when closes it disables. This could be done easily with the simple time clock.
The thermostat will not control a discharge temp as the unit would constantly go off and on (it is not a modulating make up system). So the best you can do is to have the thermostat in the pull side so that anytime the temp is below 50 being brought in the heat will function. Do you have plans when cooling as to pulling in 90 degree outdoor air?