Have HVAC Questions? Ask an HVAC Expert for Answers
What is your question?
thank you...sounds low on freon.
Clean coils....but sounds more like a freon issue
At 90 f outside you should be 75 suction, 265 head and a 15 degree delta T
I apologize but I am not currently configured for phone contact. I can, however, opt to someone who is.
ok that is much better...is the suction line colder and the register temp 15 degree cooler than room temp?
previously you said.....
Outside temp is 90 right now, temp coming out from condensor fan is 100, temp going to evap is 75 and coming out of evap is 69
is that different now?