Have HVAC Questions? Ask an HVAC Expert for Answers
If motor on outdoor unit is hot, either the fan motor or the capacitor is bad, If compressor tried to run with no fan it is probably cut off on internal overload.
Do you have a multi meter and a capacitance tester?
Lets verify we are getting 230v in and out of contactors on call for cool http://i.imgur.com/pT2mWjq.png
Compressor will not make any noise it windings have opened until it cools back down.