Have HVAC Questions? Ask an HVAC Expert for Answers
Capacitor is on the blower casing if you are referring to the indoor fan unit,
Did you find it?
How many wires to the motor?
follow the brown
OK let me check
Well there is supposed to be a capacitor on that unit
By factory it is on blower casing, has anyone tampered with unit?
Let me call Payne
You have a ecm motor, it does not have a capacitor, but you have a ecm modual mounted on back of motor with a dozen wires, you will need to replace that it is part number HK44ER155, $ 300-400
Dont forget to accept answer and rate my assistance so I can get credited for assisting you