Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue.
If my initial response doesn’t answer your question then let me know and we can continue our conversation.
NOTE: I can only get paid for assisting you if you click FINISHED and RATE ANSWER after you are satisfied with answer.
Are you ready?
Was the WIFXV used with a r22 freon condenser before?
Does the unit specify R410a or R22, as they come in both models
unit may not work as components don't have the same design pressure but if suppliedwith 2 orrifice it may be a universal unit.
Info on that unit is all spanish on the net, have you gone through the details in the manual supplied with unit?
In the installation manual you should find specifications of orifice details and installation details
There is no info available to say for sure if that will convert your unit to R410, can you revise the literature carefully for the use of that orrifice?
I tried calling tech support for that unit a westing house with no success !!!
Try tech support at a latter time, they seem to be closed at this time 1(###) ###-####/p>
Yes for sure.
Nordyne (Wh makes Westinghouse)makes this unit for use with R410A or R22 but they are different units.
The unit you have is designed for use with R22 only
The orifices are for using with different R22 outdoor units
You would need the WIFXV-60EW4E for R410
Not saying you could not use it and get by, but Nordyne does not recommend as the design pressure on the R410 is about 60% higher than the R22.
Since this unit is designed for use with R22 you will chance premature leaking due to the operating pressures.