Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue.
If my initial response doesn’t answer your question then let me know and we can continue our conversation.
NOTE: I can only get paid for assisting you if you click FINISHED and RATE ANSWER after you are satisfied with answer.
Are you ready?
Have you noticed ABNORMAL FLAME PATTERN upon startup like flame lifting and clouding up then blow out completely ?
I flame looks normal and it just shuts down...?
The issue is caused by the Flame rods. Near the 2 pilots at the front and the back. Those small rods each that 'senses' the flame become inadequate, so they need to be replaced with a new pilot assembly from Rinnai that has longer rods and better coverage.
Contact your Rinnai dealer for details for replacement parts.
Have you resolved your issue?