Have HVAC Questions? Ask an HVAC Expert for Answers
my name is Billy. So at this point the indoor kicks on but the outdoor unit does not?
so mechanically it "appears" that everything is working but the home does not cool?
while the unit is running...feel the 2 copper pipes that connect the indoor to the outdoor unit...one has black rubber. Tell me what the pipes feel like
Ex - small one dry and warm
large one dry and cool, wet and cold, regular air temp etc....
Thank you...now..I need the room temperature..and the temp coming out of register while running
Before wrapping up....is the outdoor fan running thee correct direction after changeout?
depends on motor but could be a small reversible plug or a wiring swap. Is the air blowing out the top with the leading edge of the fan blade the lowest part of blade
Ok, pending the motor is correct..
I believe it is refrigerant level.
The pipes are different temps so we know compressor is running...but the large pipe should be seating...I think you are undercharged.
Thank you for your patience and have a great weekend