Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, tell me what the room temperature is, AND if you can hear the blower running or not. AND if the unit that sits outside on the ground is running or not, we can go from there
Thanks... the system is either way low on refrigerant, or the coil is iced, and the ice is blocking the air flow.
If the coil is iced the largest diameter copper tube attached to the outside unit will be very cold or frosty.
Look for that, and let me know what you find, we can go from there
Stay in touch, that may not have fixed it,
Make sure the air filter is clean, if not the coil will get frost on it, and that will develop into ice and block the air flow.
If it was just at the frost stage, shutting it off for a while would let the frost melt but if you do not fix the cause, dirty air filter or blocked vents, it will simply frost over again then ice up overnight.
Please hold your rating until you get what you wanted from me. we can go from there.