Have HVAC Questions? Ask an HVAC Expert for Answers
Hello. yes it could be a bad pressure sensor or printed circuit card. It could also be algae clogging the heat exchanger in the boiler.
If you can send me a photo of the unit wiring diagram glued to one of the service panels, taken up close, very well focused and straight on, then post it here using the paper clip icon at the right end of the tool bar, I can coach you on an exact diagnosis.