Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue.
If my initial response doesn’t answer your question then let me know and we can continue our conversation.
NOTE: I can only get paid for assisting you if you click FINISHED and RATE ANSWER after you are satisfied with answer.
Are you ready?
Let it run 12h till humidity level drops, and check, It.s not that bad.
You have to plug your gauges Hi side to suction and low side to the common tap
Put it this way,in heat mode the red hose goes to the big copper pipe, and the blue hose goes to the other tap, not on the small copper line, you should see a 3rd tap coming out of casing right next to the valves
Got it? here is a picture open the link
Cause your in heat mode and you had it hooked up wrong is all.
Hows your pressure reading now?
NOTE: I can only get paid for assisting you if you click FINISHED and RATE ANSWER