Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue.
If my initial response doesn’t answer your question then let me know and we can continue our conversation.
NOTE: I can only get paid for assisting you if you click FINISHED and RATE ANSWER after you are satisfied with answer.
Are you ready?
Stand by, just studying both boards
can you take a clear picture of the 6 wires you need to connect and the board
Do you still need help? My name is ***** ***** different tech
T is no longer used. It was a anticipator...L is the same...it was for a light or alarm no longer used.
Are your other wires the C R W O Y?
yep, you have a newer board which does not need the thermistor wires (purple T) or the L wire.
See this booklet towards back...the T and L are discussed and the diagrams show changeout....HERE