Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, I will be rite with you.
OK send me a detailed photo
Thanks, ***** ***** the old wiring diagram, did you not wire went where, and you could use that to adapt to new wiring diagram
OK can you give me a good picture of furnace wiring diagram
Can we continue in half hour, I must leave for a short meeting
Will be with you shortly
I am drawing up a simple wiring diagram , will be done soon
OK here you go.
Dont forget to click ACCEPT ANSWER and RATE XXXXX for Assisting you if we are all done, this way I will be paid for helping you.
Hello, are you still there?
OK Heat goes on when R and W are bypassed rite at the fan center, can you take a picture
OK stand by
Did you get the t-Stat to initiate burners?
The fan on did not start fan cause furnace went in lookout because fan did not start when it should of
That is because furnace locks out on hight limit, better stop it for now, I think there is one wire that is in the wrong spot on my diagram. stand by
can you cut off power to furnace and reverse the brown for the red on fan center,
could you send me picture of your new fan center wiring diagram
Thanks, ***** ***** continue with you tomorrow, to late now, OK
Hello good morning, Here a revised wiring diagram.
Please disregard the other one. as it doesnt work. It was getting to late I guess!!
Hope it all works out for you, I was glad to assist you, if theres anymore question after you click finish and rate, you just reply on this conversation.
Sorry for the delay, drew up a new diagram this morning before leaving for work, and left out the link??
Here you go.
Use the black wire from motor, dont use blue from motor just marette the end off
Let me know how it went,
Can you click FINISH and RATE ANSWER so I can be paid for assisting you please?