Have HVAC Questions? Ask an HVAC Expert for Answers
More times than not, there is a break in the low voltage circuit.Do you have a drain float switch or anything in the circuit.Otherwise start by checking 24 v out of transformer to board.
Thanks for the pic. The discoloration is not normal as it indicates they have been warmer than normal. Lets get that meter and check our voltage though before condemning.