Have HVAC Questions? Ask an HVAC Expert for Answers
Hello, I am here to assist you
Sound like you are running on low pressure, you will need to do a supply pressure test at gas valve and outlet pressure test on the gas valve, make sure you have at least 10WC on outlet, regulator spring should be cranked about 10 full turns
As for inspecting an cleaning the power ventor you will have to get the pipe off and remove fan from unit no matter what.
NOTE TO CUSTOMER: Please take the time to "Rate" the service from the technician. If they are not rated they are not credited for assisting. If you require further information please use "reply".