Have HVAC Questions? Ask an HVAC Expert for Answers
Hi I am Luke, Check gas supply like shut off valve on gas line, gas in propane tank if it apply's, on/off switch on gas valve.
Ok, let me check
Not much longer
OK after pilot is lit the flame sensor is not reading due to either it's unplugged , defective or needs cleaning.
this is the Bryant 3 wire pilot...there is a warp switch in the side that can get weak..
You have 2 options...use a short wire shaped in a U....at the gas valve you will see terminals 1-5. WITH PILOT LIT...jump terminal 1 to 5..
If burner lights = bad pilot assembly
If it does not = bad gas valve