Series 2A P205A WNM 17270999, 24 volt, millivolt, 130,000 BTU
boliler has no vent damper, no electronic ignition, is gas pilot, Control Center R82B5D, Honeywell R822U relay, Tranformer 40VA, heating system
forced hot water 2 zone, one switch relay RA32A 1066 for both circulators:
Can you please show me how to put another switch so there is a switch for each
Can you, please tell me how to diagnose if the 40VA transformer is at fault, if I need to.
Can you please tell me how I can diagnose Honey Well limit switch L4080 is at fault if I need to. Please let me know if you can help me, if so how I can pay you with pay pal and
Thank you, ***** ***** "*****@******.*** Tel(###) ###-####xtn.5301 Thank you