Have HVAC Questions? Ask an HVAC Expert for Answers
Sounds like either a bad sequencer or bad fan relay.Can you verfiy all elements do come on?
In heat mode the fan is brought on through the heat sequencer at same time first 2 elements are brought on. If the elements are coming on that tells us the sequencer is do its job but the fan rely is not.
This is not going to a limit issue.The limit would cause elements to go off and blower on.