Have HVAC Questions? Ask an HVAC Expert for Answers
What is the issue you are having?
Sounds like a gas pressure issue. If you are propane do you have plenty of propane? Also do you have access to a gas pressure tester or manometer so we can check pressure in and out of valve?
I will be happy to guide you with this once you get the meter.There should be an inlet and outlet port on valve.If you can send a pic of valve or give me model on valve.I will show you the ports.
There should be an allan plug on in and out side of valve that you ill remove and connect a fitting to check pressures.
We should have about 14" water column pressure in and when burning about 10.5" out.
The gauge in pic will not work as it reads in psi .We need a gauge that reads inches of water column. 14" water column converts to only .5" psi, so this gauge would not give us an accurate reading.
Sounds good.Please wait to rate answer until you are satisfied with my answer and feel I have earned a rating of 3 or higher.Remember, you can continue follow up for up to 30 days after rating with no additional charges.I am here to help you solve your problem not just grab your money and run.I strive for 100 per cent customer satisfaction.If this does not solve your problem we can go from here.