Have HVAC Questions? Ask an HVAC Expert for Answers
Give me a minute to see if I have resources to verify this.
That contactor should work fine.It is actually a 240 volt contactor,24 volt coil with up to 40 amps and resitance of 50.
The OEM contactor was only a 25 amp with resitance of 30.
Never hurts to be a bit heavier duty but can not go the other way.What issue are you having?
Did not see question today.Actually thought yug got working on the 18th.