Have HVAC Questions? Ask an HVAC Expert for Answers
Hi I'm Brian and I'm here to help!
No, that air handler does not have a blower motor capacitor in the usual sense. It has an ECM (electrically commutated motor) variable speed motor. When the motor rocks back and forth like that 4 out of 5 times it is the motor control on the bell end of the motor. It could also be the blower control in the air handler though. It requires a specialized test instrument to diagnose positively which component has failed. Click Here for an example of the common failure item.
Let me know if you have further questions on this subject. Otherwise, please remember to rate before leaving (3 stars or higher please!). Bonuses are always appreciated! Thanks for allowing me to help and thanks for using Just Answer!