Have HVAC Questions? Ask an HVAC Expert for Answers
2 blinks indicates the pressure switch is open. Is this little exhaust motor coming on?
Disconnect the little rubber hose from vent .leave attached to pressure switch. call for heat, allow little exhaust motor to start, then suck on hose and see if pressure switch will close and furnace ignite.