Have HVAC Questions? Ask an HVAC Expert for Answers
Good Morning Jeff, I am Kevin one of the techs here on JA.
so your blower is not running on the furnace?
ok, so the burners light and all, probably kick off, on high limit? and as soon as the furnace cools, will go through another cycle?
and you have placed the fan switch in the "on" position, with no change in status?
I'm unable to find a wiring diagram just yet of your furnace based on the model number you supplied.
But, at the furnace, if you can :
Jump R to G ( run small wire between )
power on, don't forget to hold door switch if so equipped. Does blower start?
I would test the leads to the blower first. Is it an ECM motor? (probably being variable speed), Can you take a picture of the board and use the paper clip to attach here so I can see what your looking at?
there is a paperclip icon just above where you type your replys..... that will ask for a file or browse, when clicked.
yes, give me just a minute to look at those pics.
the number of wires coming from the blower to the board ? which plug is it in your picture?
is it the lower right corner plug in your pic?
is that a light to the left of the low voltage connections from the stat?
can see that clearly. I'm not sure if that should be on when the blower is not running. But I tend to agree with you. I would check the motor leads, (the 120v) leads.... but I'm almost convinced that your board is bad. You may as a last resort, removing the plug and re seating it.
Coleman, York, and a few others use "Source 1" parts. problem is I have a hard time getting your model # ***** So to get the correct board? Maybe if you can double check that model #, we might be able to find a board online for you.
I will need to check that , I did find a parts diagram,
parts diagram is all I can access.......
I believe you part # *****(###) ###-####
This is the only place I can see that might sell the board.
You might want to check with a "york, coleman" distributor,
here is the link to the parts manual
Jeff, I'm going to have to run.
I wish you a Happy New Year, if I don't talk to you before then......
Any other questions please feel free to contact me.
if you could before you go, leave a rating for the service that would be greatly appreciated.