Have HVAC Questions? Ask an HVAC Expert for Answers
Good Morning. I am Kevin from JA.
Sounds like your blower motor is not operating, ( this would freeze up the coil inside, and you would see it travel on the larger of the two pipes to the outside. First we need to get the evaporator coil defrosted, then I would try turning just the blower motor on, (fan switch on the thermostat), we can further diagnose from there.