Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
You need to test for 24 volts at the gas valve when the igniter is glowing. If you have 24 VAC there and no main burner ignition then the gas valve is suspect. If you don't have 24 volt at the valve when the igniter is glowing then the board is suspect