Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can continue our conversation.
Do you have an error code on the display?
What happens when you cycle the power OFF then back ON?
I have to step away for a while. I'm going to open this backup to my colleagues so one of them can help. Please don't respond (even to acknowledge this post)until you get a response from us. If you respond first it will only delay your answer. If no one has responded by the time I get back I'll pick up where we left off
Hello, first step will be to re-pressurize the boiler to 20 psig when the boiler is hot, next step will be to bleed air (in any) from the radiators.
I will be back in a minute after I locate the manual and a video on how to pressurize the boiler.
Let me know if this is the boiler you have or not and if the copper fill loop is actually in place.
If you manage to get the pressure back up, next thing to do is bleed air from the radiators if that is what you have... if you have in-floor radiant heating loops, we will take a different approach.
Let me know if you need coaching on how to bleed air from the radiators and other high points in the system, air in the system prevents water flow, and will produce the symptoms that the system is exhibiting.
We can go from there without a time limit.
Thanks, ***** ***** what I needed to know.
You can use a USA standard garden hose connector on most of those units.
Tell me what connection is at "C" and attach a close up photo of it here using the paper clip icon at the right end of the tool bar, or use the 'attach files' link to the left of your send button.
If you can include a photo taken from a low angle, looking up at the bottom of the boiler so that I can see how the plumber installed it, that will help as well.
We can go from there.
I will stay with you on this, without a time limit until you have the boiler repressurized.
Hello again, there are various adapters that will give you two female ends, depends on what your local hardware store carries.
Let me know if those directions make any sense on your end or not. Here they are again
We can go from here without a time limit.
ooops I forgot to make a link out of it
that should be a hyperlink, hopefully.
Thanks for letting me work with you. When we are finished,if my answer has been polite, professional, and thorough, please locate the 'rate your expert button' and click one of the ratings .If you still need help let me know!.
Rating will not increase your charges, nor close the question, but is how I earn my living.