Have HVAC Questions? Ask an HVAC Expert for Answers
this is generally caused by lack of air flow,,,,dirty filter, dirty fins on blower, ductwork crushed or plugged.
Can you check these things?
if you had a vent restriction it would not start. he pressure switch would fault if there was a blocked or slow vent.
Whatever you have is allowing it to run until too hot which eliminates venting