Have HVAC Questions? Ask an HVAC Expert for Answers
I will be happy to assist you today
Do you have a multimeter for troubleshooting?
Lets see what we can do without a meter. Remove the blower panel and locate the control board.Look on board for a 3 or 5 amp auto type fuse.remove it and see if it is burned.
5 is fine, but nothing bigger.Have you checked breaker?
If you have no light on board we have a power problem and may have to get a meter to troubleshoot.You can get an inexpensive one at Walmart for about 15 bucks if you would like to troubleshoot and I would be happy to guide you.
Silly question, but without a meter how do you know you have power at wall switch?
LOL. I see. does ithave leads where we could see if the door switch is letting power through to board?
Thee should be a black power wire going into the push button door switch and with switch held in power out to LINE on board
Let me know if we are getting power to board? By the way, which tester do you have?
White and black where power comes to furnace ,Then black on other side of door switch and same white
Then out of board to transformer. I have to step away a few minutes but will be back shortly
No 120 out of board going to transformer?
But you do have 120 at board on L-H and Neutral?
That is what I last sent. You should have a terminal on board marked L-H and then other side the neutrals where all whites connect.
Scroll back up and click on link I sent.Let me know if it will still open.
Try this link
If we have 120 in, but not sending 120 out to transformer board is bad and will have to be replaced
This is the board I show.I would verify before ordering though.
I am showing part 0130F00005S