Have HVAC Questions? Ask an HVAC Expert for Answers
it is a fan control out of calibration. On the front wall do you see a rectangle box..and in the box is a dial with numbers...put the first pointer at 100 and see if it runs better,,,,basically the fan is sensing heat after shut down and kicking back on....sign of an old fan switch
try 110-120...if that works then your switch is way to weak to be reliable and will need to be replaced
so after the unit shuts down and the fan cycles a few times...eventually it stops and remains dormant until new heat cycle?
Thank you..you have a bad fan switch. Yours is beyond adjusting and needs to be replaced if you want the cycling to stop.
set the "on" temp a little lower by 10 degrees...we can balance this with timing and settings
Set as follows..
Yes we have the next route but I save until the switch is adjusted the best we can...
The blower motor in bottom...are you comfortable changing speed on the blower?
Great...the wires from the blower...there are different speeds. I do not know if you still have oem motor..but we usually have red wired for heat and black for cooling...then there could be spare speeds in between of yellow, blue or orange...what is your set up?