Have HVAC Questions? Ask an HVAC Expert for Answers
Hello my name is ***** ***** will be my pleasure to assist you. if you go to the furnace look in the lower blower door for a peep hole inside there may be an led that is flashing a code. Count the number of blinks and get back with me. Usually turning the power off and turning it back on will reset the unit.
is this a furnace I cannot find any info with that model number
is it a hanging heater or a regular furnace? the blower motor is not coming on at all? Are the burners igniting?
if you take the lower blower door off locate the thermostat terminal connections and jump the R and G terminals with an unbent paper clip bent in a " U " shape. You will need to hold the door switch in while jumping it using a piece of tape to hold it down will work easier then trying to do both.
the blower should come on with it jumped out