Have HVAC Questions? Ask an HVAC Expert for Answers
Hello my name is ***** ***** will be my pleasure to assist you. You will need to take the thermostat cover off the wall plate when the thermostat goes blank and use an electric meter from the R terminal to the C terminal to verify that there is power to the thermostat if there is then the thermostat is bad if there is not you have an issue with the transformer in the airhandling unit of your system.
you are very welcome.