Have HVAC Questions? Ask an HVAC Expert for Answers
Welcome to Just Answer, my name is ***** ***** I will do my best to help you with your issue. If my initial response doesn’t answer your question then let me know and we can
continue our conversation.
You've confirmed that you have a draft issue. The question is do you have a bad switch or a weak fan or a blocked exhaust vent. You can check the vent and also the vac tubing connected to the switch. Be sure the tubing is not kinked, deteriorated or doesn't have water in it. You can also poke a paper clip into the port where the tubing connects but not into the switch connection. If all of that checks out the next thing we would do is put a manometer on the exhaust to check the actual draft pressure but you aren't likely to have a manometer and they are expensive so replacing the switch is one other option since it's less money than a manometer (or a new draft fan) and it is a likely culprit.
Then if none of the ports are blocked and the vent is unobstructed then the the remaining possibilities are a weak fan or a bad board. You need to put a manometer on the draft to determine which one is the culprit. Both parts are too expensive to guess.
A phone call is an additional charge and there's not a lot I can add to what I've already said.