Have HVAC Questions? Ask an HVAC Expert for Answers
how long are you holding the button down?
thank you...is this the first time starting for a while? Or was there a loss of fuel?
right now....what lights if any are lit on the control?
ok, do you see where the 2 thermostat wires attach? tr and tw
ok, you have a power/control issue and the fault is not on the oil burner. Do you see where the thermostat wires attach on the aquastat?
use a short wire or paperclip shaped in a U...and connect the 2 terminals
thank you...and no operation?...also have you checked breaker that feeds L1 and 2 on the aquastat
if there is no display on the aquasmart there is either no power to it...or the control is bad.
We need to see if there is 120v on L1 and L2...do you also have a zone panel?
there should be a zone panel that the thermostats attach to.
But if things were installed correctly the 120v feed goes to the aquasmart and also leapfrogs to the zone panel..here is the deciding factor...
If L1 and L2 on the aquasmart have 120v then the aquasmart is bad. If there is NO 120v on L1 and L2..then we have a power supply problem to aquasmart
there is commonly a switch before the aquasmart also...but unfortunately your issue is either power or bad control which means you would be calling for service regardless....I thank you for your patience
you are very welcome...just rate service and I will close