Have HVAC Questions? Ask an HVAC Expert for Answers
If you can take a well focused, well lit, close up photo of the wiring diagram glued inside the blower service door, I can mark it up with trouble shooting directions. Include a photo of the printed circuit card in the same compartment where the thermostat wires attach
You will need a multi meter do do a few tests.
Use the paper clip icon at the right end of the tool bar above to attach the pictures.
We can go from there.
Hello again, tell me please about how old the furnace is...it may be too old to have a printed circuit card in it, and also too told to have a wiring diagram available on the web.
Let me know about that, I will see what I can find on the web its not too old. There is another issue with old furnaces, they leak carbon monoxide in many cases, that can ruin a persons health and is even more damaging to children.
Thanks, ***** ***** about the time they began using printed circuit cards.
Look under the burners and use a long handled spoon to drag out the rust under each burner, tell me if there are any larger chunks of rust or a lot of rust and tell me if the flames in any of the burners change when the blower starts... look very very carefully for any change in the flames... that will tell us a lot.
The cause of failed ignition is generally a bad spark or glow plug igniiter module, or a bad gas valve. If you can follow the wires that attach to the pilot light back to where they came from, that will be the ignition module. It will have a brand name and model number on it in most cases.
Then there is a chance we can order you a new one... there is about a 50% chance that will work.
Without a wiring diagram I am at a loss on how to coach you any more effectively than that.
It is common that older furnaces develop cracks in their heat exchangers, and that ruins the lives of many people... with older furnaces a few cursory checks are *vital... if you find large chunks of rust under the burners, the heat exchanger is most likely cracked or soon will be cracked and a serious hazard to your health... in that case you will not want to spend any money on repairs and will want to replace the furnace.