Have HVAC Questions? Ask an HVAC Expert for Answers
do you have a brown and a brown with white strip hooked to its own capacitor..and then the 2 hots direct to contactor?
is the capacitor a fan only with 2 sets of terminals or a dual cap with 3 sets?
and no other wires on cap...just the 2 browns?
one hot to one side contactor other hot to opposite side....2 browns to cap? and NO other wires on cap for fan?
ok on you motor...what are colors and I will tell you where to land..and also is rotation correct?
ok this will be quick...just tell me if you know what the contactor is?
black motor wire to contactor T1 terminal
white wire to contactor T2
2 browns to cap green to cabinet ground
does the new motor say on the side it takes a 7.5 or was that in the original?
is it a 7.5 330v 0r 7.5 440v and what is new motor rated for?
was this changed from a dual cap.
see this link and tell me if your unit
can you post it here using the attachment link at top of dialog page. I am very sorry to drag this out...I know you dont feel well. Would you like to continue later?