Have HVAC Questions? Ask an HVAC Expert for Answers
If the fan is running then the draft pressure switch is a likely culprit. It's disk shaped and has 2 small diameter vacuum hoses connected. It has 3 terminals. You can try jumping the NO & C terminals after the fan is up to speed (not before). Let me know if that initiates the ignition sequence.