Thanks for the excellent detail.
The compressor is wired incorrectly.... the condenser
fan may be wired incorrectly at this point also.
Line 1 runs directly to C on the compressor and also to the C terminal on the run capacitor.(not the herm terminal on the capacitor... C is the middle terminal on the capacitor.) Let that soak in for a while.
The Herm terminal on the capacitor runs to S on the compressor (that is the start winding in the compressor.
Line 2 on the contactor runs to R (run winding) on the compressor.
Attach a well focused, well lit photo of units wiring diagram, taken close up and straight on... using the 'attach files' link at the bottom left of your reply box, so that I can verify that.
We can go from there.
Please rate my work so far, so that I can justify spending time above and beyond what is allowed for by a simple answer.
We are on the honor system here. If you need anything else, just let me know. You can continue asking follow-up questions at no additional charge.