HVAC Questions? Ask an HVAC Expert for Answers ASAP
Sorry bout that...dont know why it was like that for over an hour but perhaps the problem was someone wanted to answer it and we wanted you...yes the problem is turn heat on and it comes on for a second while the light flashes two tmes then pauses and comes on solid,,,,the light, the furnance acts like it is going to actually kick on all the way since the tubes light up and then it instantly kicks off and flashes 8 times, pauses and flashes 8 times again...recall from previous that there was a new thermostat installed and then you told us that it was actually the control panel since the test you had us do led to this and then you told us how to bypass it so that we had ac if we manually turned it on and off, now with new control panel the a. c is good running without us doing it manual, but the issue listedabove is with the heat and heat is what we need
Heading there to now, door panel is already off so he is going to remove the wires....just a second please
yes light comes on
just minute hooking up jumper...paper clip...
it kicked on flashed twice and then stayed solid..fan constitnly ran til i turned the power switch off
r to g does this....kicks on stays solid and does so til i remove jumper with fan as well ...sorry redid to make sure this was correct and now r to w with jumper kicks on flash twice stays solid and runs til shuts of switch even if removed jumper it still did until shut off by main power
what is it???switch u had me tape down? i doubt that is what you are talking about so tell me where this may be found....general area or so
i thnk there is two of these hockey pucks things as they both have a white rubber tube coming from them....and two wires on each as well...???
ours has two,,,,one for each burner maybe?
i unpluged a wire from one of the switches, and turned main power on and light stays solid....????
i also put the wire i unplugged back into the switch and unplugged the wire from the other hockey puck switch and the same thing happened when i turned on the power....the light stayed on solid
the furnace turned on.....when we r to w with jumper and then turned power on while jumper r to w and replaced the wire to the switch that looks like hockey puck, the light stayed solid and then we heard click and pilot cdame on burners ignited no code and since we have open flame so i took jumper off and turned power off since not sure what wanted me to continue to do....
THis worked though we had it on....
unhooked a grey tube that goes to the hockey puck or pressure switch and then blew in each one and put them back on ....to do that i have to hook up the thermostat switches again correct? THen try to turn the heat on like i would if nothing ever was wrong? just blow threw each of them rbber tubes and hook it all up? just checking to make sure i follow correctly
oh okay,,,give me second to hook it all bakc up and listen for the click when we blow and draw air doing either or both til isten for a click....just a minute or so
This all did not work it all came on just like before and shut off as before and then it gave the 8 flashes after it shut itslef off again...could the prob be the thermostat? When the problem was just the ac and the people came out thnking it was the thermostat and brought in a new one they were arguing about how it hooked up...also on the thermostat to the board on the furnace is there suposed to be a jumper going from c to y...on the actual furnace? thats the way it was wired...i dont know but there wil be a tip for the size fo the paymetn since this is five or free just ot let yu knwo we dont expect u to do allthis for nothing
going upstairs to look at the thermostat....was downstairs with the furnace...here we go thanks so much this is alot esp online but its cold and im at my last straw here....need you to come out to our house...ha ha...
therm upstairs with it off goes red to r, yellow to yy2, and green wire to g, and white wire to the ww(this one is hard to read so if it has slash or number after it i cant tell nnot in color imprinted) my concern now is with the furnace when i took off the old contol module there was two wires coming off and the red goes to c and the white wire goes to y where the yellow wire goes as well this is what i was scalling the jumper to y to c...wanting you to understand that there is two wires coming off of one loom or hook up on the furnace control module
ok at therm i twisted the red wire and white wire together and hcekced to make sure that on furnace the red is on r and the white is on the w....the above checks out as well regarding the issue on outdoor ac to the therm as well so now ????
when those two are together there is no code when i turn it on ...it was running and stayin on no code....i turned off the pwoer on it and came back upstairs to type to you
I cant believe that...but should go with gut huh? Even had we had pinpointed the thermostat as being messed up somewhere along the way we still would of had issue with the stuck pressure switch....so thank you so much and also the first time when you gave us relief with air by tellin us to replace the control module...funny how you can fix the problems that four men, professional supposedly, and you do it online! To bad we cant just contact you straight out when we have problems or have friends or family with problems as you really know what u are doing and we are very grateful and now warm too! Thanks for sticking in there with us esp we calling things hockey pucks haha