Hello R.G. I was told by a service rep that my old board needed to be replaced. So I purchase a new one and installed by following the directions. to answer your questions. Red wire to Red terminal, Yellow wire to yellow terminal, white wire to white terminal, 24v common to blue wire and green wire to green terminal. I have a volt meter
It did start up on test though
Correct I taped the switch flip on the power switch
ok will be back in three minutes
26.9 volts and the fan is running
no reading from 24v to white but my burners are on and the blower is pumping out the heat.
I check from common to R and I had 25.9
common to white 25.6
i missed read last time my bad
I know I should check the AC but I'm confident that they are working. I have been cold for so long all I want is heat right now R.G. you are Ok in my book sir.
Ok I'll check out the AC give me a minute to warm up
I'm good its after midnight I work on the AC tomorrow. Thank you R.G.