Have HVAC Questions? Ask an HVAC Expert for Answers
I have a volt meter that is rated to 300 V maximum
I am not.
ok Trane XE 1600
Just got to the board. I have a flashing red "status" led on the board. I cant tell which terminal we are trying to figure out if it's putting out power. Picture is small and I can't enlarge on this end
Ok. I located where the black fan wire goes into the board. how do I test for power?
I put the AC on, unit comes on about 10 seconds later. Fan does not come on. Unit runs for two minutes, then shuts down. During this time I put meter on with red to black on terminal and black to red wire on contactor. My meter reads 60 on the DC scale or 2 out of ten on AC scale.
went with the bypass and the fan makes a bad sound and when manually turned it goes slowly for a bit and then stops. Fan motor seems bad, time to call in a technician