Have HVAC Questions? Ask an HVAC Expert for Answers
it wont let me reply
They sold me a dual capacitor when I bought the motor, It says to put the Brown and Brown w/white which I called the Gray and gray w/ white to the CAP.
You don't have permission to access "http://www.justanswer.com/hvac/7tm32-hello-need-help-my-hvac-condenser-motor-went-bad.html" on this server.
Im trying to upload pictures
do you have an email address I can send the pictures to?
the new one does not have markings on the terminals
Hello again, you need a good multi meter with a 'micro Farad' setting on it, (uf)then you can check between the center terminal and each of the outer terminals... the side for the fan will read 5 to 7 micro farads. and the other side will read about 5 times that for the compressor.Or you can take the capacitor back to Graingers and ask them to help you identify the terminals.You could very easily have it hooked up backwards without any markings on it...
How did they know which capacitor to sell you, did you take the old one in for a match up? however the old one may have had the wrong uF rating for the new fan motor.. I need to know what the UF ratings on the old capacitor were and what they are on the new one..those are printed on the side of the capacitor.
Let me know what you find, we can go from there.Phil