Have HVAC Questions? Ask an HVAC Expert for Answers
It was running about 1 month ago. We turned it off and it wont come back on
Yes I have both
I am unclear. Are you saying to test the R wire to the C wire or are you saying to test the R wire to the metal housing of the air handler to measure for 24 v? Also just so you know the thermostat on the wall does not use C wire. I was told this is only for power to the thermostat and mine runes off battery power only.
continuity is all I get. No voltage
power is to the unit and it is a Goodman Manufaturing Corp Model no. a24-10
I do know where the transformer is. Also I do not see a blade fuse anywhere.
Ok. How can we do that
So just touch the volt meter to both sides of the transformer correct? And I should have a 24v reading?
Ok I checked the 24v side and there is no voltage coming out.
yes I had also checked the other side while i was up there and I did get a reading for 220
OK. I was thinking thats what you were going to say lol.. I will replace it tomorrow once the supply house opens. Thank You for your help on this issue.
Attachments are only available to registered users.