So, what do I need to do?
Do you mean on the guage there is no pressure showing?
I think so, the dail is not between the ranges it should be.
I get the F.25 error
I have switched it off and on a few times but nothing.
what is the guage reading?
I have read some of the materials and am thinking it needs to be 'filled' but not sure how this is done
will take a look. brb
Can you trace the water supply pipe to the boiler, not the ones that supply heat, but one that brings fresh water
its between the 0 and 1 so 0.5
there will be a valve on this pipe, that we can open and raise the pressure
Good,ok that is too low
I am on my pc, need to move to the ipad so I can take you with me. will be right back
do you see a valve close to the boiler
it will either have a lever or knob
IS the red cap thing on the pipe you figure is the supply?
the red knob may be pressure relief Valve, opposite of what we want lol
black small lever
yes that might be it
sorry your connection keeps going on and off, hence the delay
Yes that lever, you can pull it up or down (depending on how its situated) and if there is pressure there, it should allow water into the boiler, watch that guage and you can bring it to lets say 1.2 bar for now
hopefully it shut off once its flowing, you may have to tap it off
once the temp is up, you can add a little more if it needs it, it shouldnt be higher than 2 bar, and not lower than 1