HVAC Questions? Ask an HVAC Expert for Answers ASAP
Russ here what probem are you having.
1 brown to each side of capacitor . You should have 1 brown with white stripe.
Connect the two white wiresto that side of capacitor with brown/white. Tape off blue and yellow wires. Russ
put 1 brown on 1 side and the other on the side with the whites
Yes You should have a brown/white. White wires can go to that terminal or you can just connect the whites seperate.
Did you get last reply. Russ
when I do that the motor just hum do you think the capacitor might be bad
If you have it wired correctly. 1 brown on one side of capacitor and 1 brown white on other with your white common wires attached it should start. If not replace capacitor. Russ
Size of capacitor is on side. It will say something like 5uf 370VAC or 7.5uf. Russ
it does would that be why it run's with both brown wires together and both white wires hooked on the same side